Promat PromaSnap Floor Waste System
Floor wastes in wet areas are notoriously difficult to seal in the event of a fire. The lack of a pipe stack above the floor level means that the floor grate offers little protection from fire and smoke once the pipe work has burnt through.
AS 4072: Part 1 demands that the fire resistance test of floor wastes must be conducted on pipe work that is identical to the installed configuration. PromaSnap Floor Waste System has been tested for floor waste applications to AS 1530: Part 4 and AS 4072: Part 1 for 120 minutes with uPVC pipe and fittings.
PromaSnap Floor Waste System has been designed to not only provide a tested system but also provide an effective, simple solution for water proofing and the levelling of the screed for tiling and water flow from the floor.
The system consists of a PROMASEAL PipeSeal to hold pipe work in place. If the slab depth is over 125mm deep, the length of pipe required is 75mm less than the slab thickness, e.g. for a 300mm slab depth a 225mm length of pipe is required.
For slabs less than 125mm thick, reduce the length of the spigot on the PromaSnap Floor Waste System that connects to the pipe. To ensure the puddle flange is level, it may be prudent to cut the pipes slightly less than this 75mm.
PromaSnap is manufactured entirely from recycled and recyclable material. PromaSnap® Floor Waste System is certified under the WaterMark Certification Scheme.
FOR TECHNICAL INFORMATION PLEASE VISIT http://www.promat-ap.com/en/products
Be The First To Review This Product!
Help other Passive fire warehouse users shop smarter by writing reviews for products you have purchased.